Continuum found and added both third party chiller controllers, RLE LD5200. When a send to database is executed however, no objects are added to the Continuum database.
- RLE LD5200
Some BAS systems use a 16 bit identifier while Continuum uses 32 bits.
Problem resolved updating the third party controller firmware..