In an MP-V controller, Box flow is reading air flow when the VAV damper is closed
EcoStruxure Building Operation
Building Operation Multi-purpose VAV FW v2.00.01.00016
Building Operation Workstation (Version 2.0.x or later)
Confinguring the MP-V Box Flow Zero Point WebHelp article in Building Management System WebHelp is missing steps needed for MP-V with firmware version 2.00.01.00016.
In addition to the procedure described in Configuring the MP-V Box Flow Zero Point, two additional steps are required to zero the Box flow on an MP-V using firmware version 2.00.01.00016.
Under Flow Balance Data...
The Box Measured maximum flow must be an appropriate value based on the box size.
The Hood Measured maximum flow must be an appropriate value based on the box size.
Once the procedure in WebHelp is followed and these to settings are configured, the Box Flow will read zero when the Velocity Pressure is below the Minimum value setting in Velocity Pressure properties.
... View more
On a cold start, the i2 or b3 controller does not retain the configuration stored in flash memory.
The controller error log shows a 0x000014fb error.
12 E 01/01/1989 00:02:10.00 0x000014fb 0x0928ab00 0x019085a6 0x1442000c
Continuum b3 Controller
Continuum i2 Controller
i2 and b3 controllers must compile the controller configuration prior to backing the configuration up to flash memory. An invalid configuration will prevent the compilation process from completing, thus preventing the backup process from succeeding.
The most common causes of OMS Backup failures are
Plain English programs that contain errors.
Input or Outputs that are configured without a channel number.
Correct any configuration errors.
Initiate a backup of the controller configuration to flash memory.
Verify that the backup has been successful. There should be no 0x000014fb errors in the controller error log.
... View more
All efforts to move a Continuum Virtual License from one host machine to another are unsuccessful.
The license type is not shown as Re-hostable in the Sentinal Admin Control Center webpage.
The license type is not shown as re-hostable after applying the Re-hosting upgrade activation file received from Andover Upgrade Services.
The error Invalid Recipient information, process canceled! is displayed when entering the recipient id file (.id) in the RUS Key Utility.
The HaspRuntimeForContinuum.exe is the wrong version.
Contact Andover Upgrade Services and provide them with a new host information file (.c2v) produced using the RUS Key Utility.
On the host from which the license is to be transferred...
HaspRuntimeforContinuum.exe is the most current version available on Exchange.
Rus Key Utility is the latest version available on Exchange.
Contact Product Support Services for assistance.
On the host the license will be transferred to...
The most current version of HaspRuntimeForContinuum.exe must to be installed prior to using the RUS Key Utility to generate the recipient fingerprint file (.id).
The HaspRuntimeforContinuum must be installed As Administrator.
On the host licensed host…
HaspRuntimeforContinuum.exe is the most current version available on Schneider Electric Exchange.
... View more