Regarding the NetBotz wireless Temp/RH% sensor,
It's noticed in different sites that this wireless sensor goes offline and gives a disconnected alarm and just when we restart it (Turn it Off and On again) it works fine and this happens repeatedly and noticed in more than one site.
And one of these sites there was only qty:2 of this sensor and each one configured on a separate netbotz which are installed in different floors. and the sensors installed on the front door of the rack which the netbotz is installed inside.
So, i'm asking if there is a specific configuration or concerns which should be considered while installation or configuration phases.
If anyone faced this problem before and it had been got resolved or any one have any recommendation or concerns, please advice.
Not the same issue, but we have similar problem on one site when sensors lost communication with coordinator.
Placing coordinator outside of the rack where Netbotz is installed with USB extender solve the problem.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!