This question was originally posted on DCIM Support by johnhill on 2016-11-12
I have 3 A link sensor connected with NB 570. Only 2 sensor shows into advance view. third sensor is not showning into advance view.
When we check the sensor it shows the value under it,s led.
This answer was originally posted on DCIM Support by John Thompson on 2016-11-14
I presume you are talking about the AP9520T/TH sensors?
Have you connected them in a daisy chain as per the document below?
Are you using CAT5 or CAT6 cable?
Did you install the Terminator on the OUT port on the last sensor?
Did you give each sensor a unique A-Link address using the DIP switches?
This comment was originally posted on DCIM Support by Steven Marchetti on 2016-11-14
Hey John(s), You may also want to try to connect them one at a time to make sure if one actually has an issue, deleting them from the interface as you test. Test with the same cable each time and if you have any sensor pod 150s, take them out of the picture. Depending on how many, they may be drawing power down. Steve
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!