Thanks for your assist Jean-Yves, the mapping issue has now been solved.
There are few mistake i had made,
1. as you mentioned i need to select "build a SCD file" instead of "Select a SCD file".
2. the CID file IED name need to be match with the one on M580 NOP300 side for mapping.
3. I need to use Ed2 in both side for this project as HU250 support Ed2 only.
Also would like to thanks Yves CHOLLOT and Tom Berry for getting me the configuration instructions.
... View more
We are using the "External Reference" function inside the "IEC61850 configuration tool" to set up the IEC61850 server side mapping.
Please kindly find the attached photo that we don't know how can we drag the "External" point on the left side and "Internal" Data objects" on the right hand side to the center to compete the mapping.
We using Easergy Builder in Select SCD mode and then importing the CID to the M580 as attached pic.
The T300 expert advised us to use a <IED name="IED_M580" instead of <IED name="IEC61850".
But we have found that on the M580 side, the "Internal" Data objects" name on the captured pic cannot be changed, and as it has been named as "IEC61850". Would like to ask is this the reason why it cannot be map together?
Second question is does the Edition 1 / Edition 2 matter for this case? as i have found that HU250 is only supporting Edition 2?
we are appreciated for your help.
... View more