How many concurrent Modbus TCP connections are allowed on the PM5000 series meters with Ethernet?I really hope more than 1 client! 🙂
Is there a simple formula for calculating how many days of logging is available in Datalog #1 when configured at 5 minute intervals and all 16 channels of logs are used?
In the PM8000, there are setting for Current Swell. This is a new feature for an ION meter. Can someone please define this for us? We are having a hard time I understanding what electrical meaning this has as it used to cause a lot of alarms. The new…View more
I am looking for the location of the PM8000 Firmware and ION Framework files for the Various Power Quality Standards.
Matthew WatsonI was pretty sure I read that it did but I cannot find any reference to it. I think it was something really silly like "data recorder depth: 1" but I cannot even find that.Can anyone advise?
What happened to Power Launcher? Is there a one stop shop for configuration utilities?
We have a situation in a utility substation with CT’s ratios of 600:1A but the overcurrent max CT ratings are 1250A on the high side so we are looking just over 2A for the max current at the meter. I’m assuming we should be ordering the 1A calibratio…View more
When can we expect to see the Modbus Gateway functionality in the PM556x meters? I know this is on the roadmap but we're banking on it for a few projects and wondering when we can reliably say it will be available in Wave 2?
Find more articles tagged with: pm5560
As you can see from this thread () - there are still those of us who have situations where we are using a number of ION protocol meters (timely with the PM8000 release next year) like the ION 7330/7350 and because of various reasons (like the inclusi…View more
|Date Last Visited||
2021-03-16 02:01 AM