This was originally posted on APC forums on 5/1/2013
Hi Guys, just want to verify if the battery module of SURT is below 100Vdc ( 98.9Vdc to be specific) it can't power up the unit right, even the UPS was plug to the AC source?
This reply was originally posted by Jonathan on APC forums on 5/2/2013
Our SmartUPS RT 3kVA and above units uses a 192V dc system, this 192V dc uses pairs of 96V dc battery packs and the minimum voltage that is required for it to be recognized as good is ~85V dc.
This was originally posted on APC forums on 5/3/2013
Hi Jon P
Thank you for the clarification...
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!