This was originally posted on APC forums on 11/10/2008
I'm trying to configure a couple of SYA16K16Ps that have 2 SYPD3 in them.
We're in the US, and are currently using NEMA 5-15 cables @ 120V to the servers and storage units.
I want to now change over to 208V on all the servers.
I've looked around, and I see that I can use the APC AP9566 PDU with the SYPD3.
i.e SYPD3's L6-20R to AP9566's L6-20P .
However, the AP9566 has (12) IEC 320 C13 on the output side.
Would I just need an IEC passthru cable to connect power to the servers?
Can't even seem to be able to find those.
Or am I missing something here?
If so how are people here running their standard issue US devices @ 208?
Message was edited by: a_0_0
This reply was originally posted by Angela on APC forums on 11/11/2008
oh ok i understand.
glad you found what you needed!
This was originally posted on APC forums on 11/11/2008
The servers have 320 C14 chassis sockets on them.
We've been using your basic C13 to NEMA 5-15P.
In any case, I think I've found the cables I'm looking for.
We have a few of this cable already.
The information was just not as readily accessible on APC's website.
i.e. it wasn't listed as an option for the Symmetra LX .
Thanks for the reply.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!