When opening I/NET on a secondary monitor, and open the point control window of I/NET summary for a digital output, the drop list for the point doesn't work. Nothing is shown in the drop list.
EcoStruxure Building Operation,TAC INET
There is a 3rd party system dll file out of date for I/NET.
- There is a 3rd party system dll file under the folder C:\Program Files\INET Seven\Program Files (Program Files (x86)) if for a 64 bit Operation System called SftBx32.dll. Click here to download the new dll file and extract it.
- Close I/NET IO Server and SmartStruxure Enterprise Server
- Copy this new dll file and replace the old one under that path.
- Start I/NET and SmartStruxure again, and it should work now.