This question was originally posted by Sajith on APC forums on 9/26/2011
We have installed subject UPS in our customer site.
Wiring was done for 3 phase input and supplied to UPS as L1(Red), L2(Yellow), L3(Blue) configuration and the UPS was working fine. But now the customer has changed his mind to use single phase only. In that case can we use the same input by using L1(Red) only and disconnect other phases (L2-Yellow,L3-Blue)?
Thanks & Regards,
This reply was originally posted by Chris on APC forums on 9/26/2011
Yes, you would use L1, neutral and ground only. The link to the manual for this UPS is below. It explains the electrical requirements for both single and 3 phase.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!