This question was originally posted by Kelum on APC forums on 3/29/2011
We have several SUA750 UPS, when we replace new batteries and gave a load to test, After few minits It alarmed continuously like overload. Need to reset anything. What is the procedure for battery replacement?
This reply was originally posted by Kelum on APC forums on 3/30/2011
we have already calibrated the UPS, according to the standard procedure ,But the problem is still on going . The rated UPS(SUA750I) capacity, around 540Watts, we applied dummy load, around 300Watts. after few seconds, battery level led bar flashing and contineous beep sound.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!