This was originally posted on APC forums on 8/14/2007
Ran this test the other day for our own use, but some of you may find this information useful:
Model: SU1400NET, rev week2, 2000
Energy use: 178kWh/yr
UPS inverter efficiency (with fully charged battery)
Load: 210W, 800W, resistive, to represent modern active PFC loads
relative load: 22% and 84% of 950W
82% at 22% load
84% at 84% load
On battery quiescent power consumed: 39.3W
nominal input: 24V DC
cooling: forced air
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in