I have mounted the sensor on the wall 160 cm above the floor pointing directly at my desk at the office.I am sitting 280 cm away from the sensor.I have set the sensitivity on the cccupancy sensor to 100%I have to move around quit a lot to get the sen…View more
Find more articles tagged with: smartx sensor
I need to be sure that the values are retained even after a power cycle. That only seem to happen when the retain level is set to "Cold start". If I create multible BACnet values and I want to change their retain level, then I can only see it is poss…View more
A question to terminal 2 on the MP-VI can see the terminal is marked with a ground sign.Are we supposed to connect a 24VAC phase to termianl 1 and the ground to terminal 2?What about the 24VAC Zero. Where are we supposed to mount that?
It might be me... I dont understand this drawing on page 4 in "SmartX Base_Z207549-0A.pdf" According to the manuel, then the address should be 1 if both switches are UPThis is not correct. They have to be DOWN UP - UP : 4UP - DOWN : 3 DOWN - UP : 2DO…View more
Find more articles tagged with: sensor documentation
I have created 1 Room Unit Device.Select the Room Unit and select duplicate, give the new names and click OK.The result is an error messageI also tried to Copy / Paste the Room Unit..The result is an error messageIt seems it tries to copy the room un…View more
Are there any plans to have a remote LCD display? This could be nice to have during commissioning where the controller is placed in the ceiling and you need to check out the IO.I am thinking of a cable (3 meters) with a LCD connection in both ends, j…View more
Here is what I do:Create the MP-C using Device discoveryUpload all objectsChange to database modeCreate a folder in the Application folderChange back to online modeDownload imageDownload all objectsDelete the MP-C from the Bacnet IP networkCreate the…View more
I have created the following in my MP-CTemperature Input (Ub1)Voltage Output (Ub2)MPx Function Block ProgramTemperature Input (Value) is bound to FBP and FBP is bound to Voltage Output (Value)Temperature Input, Voltage Output and FBP output is placed…View more
How can it be that the Relinquish Default & Priority 1..17 doesn't have a Unit, when it has been set for the main property?If I set Unit for Value, I would expect that Relinquish Default & Priority 1..17 inherited the same Unit.
|Date Last Visited||
1 week ago