In the various Schneider Config blocks, are there Cold/Cool/Warm start
retain value selections?
Example: An AV block that we want to use as a setpt which will maintain
its value after a power cycle similar to EBO workstation programming.
According to the BACnet spec, the value in Relinquish Default shall be stored in a non-volatile method.
So if you need the value of a setpoint to survive a power cycle then I recommend storing it store it in Relinquish Default.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in