We have an intermittent fault via communication on the XTU300, but when looking at the XML the fault isn't there any more.
The fault has been resetted.
Even with a communication reset it won't go a way. (I have send FFFF to register 10)
Does someone have other suggestions?
Thanks in advance
I believe we solved this question via email-
If someone has similar issue, specifically when there are a lot of vigilohm XML, XL, XD308c connected to the interface, please get in touch with me.
Symptom is that there are intermittent communication losses between the interface and its slaves. Communication is restored when the interface is power cycled.
It's not the seem we discussed via mail. This one doesn't lose its measurements.
But I can put logging on the communication of the bus to check if they occur on the same time.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!