Anyone experience this or know why I would be seeing white smoke come out of the pm 8000 on initial startup of the PM8000 after install? It doesn't continue to blow smoke but for the first few seconds it does. Is it a residue burning off the equipment or?
I've seen one smoke because the installer had put the CT into the S1, S2, S3 (digital inputs) instead of the CT inputs.. He changed out a PM500 and on the PM500 the CT inputs are labeled S1, S2, S3 😉
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!