Thanks & Regards,
Yes you can set up the ComX 510 to log data from the devices downstream of the Link 150.
The ComX connects to the Link150 as any other ModbusTCP device. Once connected you can discover the downstream devices.
You can connect up to 64 devices in total. I have no idea if there exist a calculator that tells you for how long you can store data. I guess that depends on the log interval and amount of devices.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!