It was observed that ION 7550 MD controller to Power Logic (Schneider) SCADA values were freeze,We have reset the power supply of the meter after that analog output channel 1&2 0-20mA ports giving 36mA and this will effecting the our load shedding program.
Please advice for the solution and reason why we are getting analog output as 36 ma.
This is posted in the ION Setup section. You should probably post it to the Power Meter Hardware section so the right people will see it.
Seem like overload condition. 0 to 20 mA: 500 Ohm load Max from datasheet. Check your transducer input impedance as well.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!