Hi all, I have 2 questions re the PM8000:
- I'm daisy chaining the coms using the dual Ethernet ports (6), will the down steam meters go off line if one of the meters loses power along the chain?
- How long does the meter hold its settings once it loses power?
-Yes, the downstream meter(s) will lose connectivity if the upstream meter loses power. The intermediary meter is acting as an active network switch.
-Meter settings are stored in flash memory and should last indefinitely (i.e.: many years) without power.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in