In the registers table of the PM8000 we have the register 54395 dedicated to display if the configuration of the frequency is 50Hz or 60Hz.
If I read the this register in INT16 I got -1 (1111 1111 1111 1111 in binary).
It is normally 1 or 0 in INT16 why it is -1?
It is written that this register is in R/W and I tried to write 0 (50Hz) and I got a modbus exception answer code 512.
Should I need to use a protected command in the same way as PM5000 but it is not mentioned in the table of registers of the PM8000_Modbus_Map (excel file)
In the web page the configuration of 50Hz Vs 60Hz is working fine but the customer want to perform that through a com Modbus configuration.
Thanks for your help.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in