I have a customer with quite a few PM8000's installed. They replaced a lot of PM500 with PM8000, so in many cases they do not have a 4th CT installed for the neutral conductor.
Is there a way to get the PM8000 to calculate the neutral current when we are not measurering it?
Best regards, Michael
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!