I hope you all are well.
I have a PM5563 din rail mounted energy analyzer with 02.04.02 firmware.
1. I connected PM5563 from my laptop via ethernet
2. I used Web (chrome browser) with default IP 169.254.0.10
3. I changed the IP as 192.168.1.10
after that, I cannot reach the EA.
I think I need to update firmware but how? I can't even reach it
do you have an idea to solve this problem?
Hello @nobia ,
When you changed the IP address of the meter, did you change the IP address of you laptop to be in the same subnet? This is a combination of the IP address and subnet mask settings.
Eg IP address 192.168.1.10 with subnet mask 255.255.255.0, would require your laptop IP address is 192.168.1.xxx to be able to talk to the meter.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in