We got an issue with PCSP that the IP Address of PCSPs changed every time powering off/on the unit. The unit showed "Battery level is low" as below:
I couldn't find anything related to this issue from Trouble shooting file. Please look into it and give me some notes.
Thanks in advance for your support.
At looking at the date on the HMI. It looks that you have to upgrade the firmware
No sure about what is the current HMI firmware installed, however the last released one( which works with DSP Version 001.006.***) primary purpose is to correct the issue of unit losing the static IP address after a power cycle which is associated with the SRAM (CRC Error) message.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!