Hi Robert Lee,
I need help about ION7650: I need to set the device to capture a waveform on external trigger, for example, with trigger on digital input. Also, I wish to set the the depth, format and delay cycles.
Do you know how to do with ION Setup?
To set format and delay cycle set the Sag/Swell and Transient module.
To set the depth set the waveform recorder module.
To add trigger from external digital input look at the Pulse Merge module name Wfm Tg Mg-Sg/Sw and Wfm Tg Mg-Trnst
there are empty inputs you can add trigger into them. Note that pulse from digital input will be 1 cycle delay.
See ION Reference for detail operation.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!