Hi Robert Lee,
I need help about ION7650: I need to set the device to capture a waveform on external trigger, for example, with trigger on digital input. Also, I wish to set the the depth, format and delay cycles.
Do you know how to do with ION Setup?
To set format and delay cycle set the Sag/Swell and Transient module.
To set the depth set the waveform recorder module.
To add trigger from external digital input look at the Pulse Merge module name Wfm Tg Mg-Sg/Sw and Wfm Tg Mg-Trnst
there are empty inputs you can add trigger into them. Note that pulse from digital input will be 1 cycle delay.
See ION Reference for detail operation.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in