Please help me configure the Relay output of ION7650 which requires to have one pulse output for every 15mins Demand (KW).
I am having a challenge on what source to use as a trigger for the relay output, using ION setup for this requirement and there are no power monitoring software for this project.
Please help me resolve this requirement.
Thank you very much!
The Interval End output of the Sliding Window Demand module can be connected to the Pulser module then set the port to any relay you want.
The default framework has provided this function already(as I remember) you just go to the pulser module then assign the port.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in