I have question regarding to iEM3210.
How log the maximum distance of cable if we use hardwire cable connected from intelligent manager to iEM3210?
If the needed is within 200 m, is it the pulse output still detected?
Thank you in advance.
I would say that 200-300 meters will not be a problem - perhaps even higher.
It all depends on the cable used and you need to maintain the voltage between 5 – 30 V DC (as stated in the user guide/installation guide).
Use twisted shielded cable on long distances (0.75mm^2 / 1mm^2) and calculate the voltage drop: Voltage Drop Calculator
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in