We have a client possibly interested in ION9k upgrade from 8K.
I cant seem to find any Class 0.1S CT's here in Australia... given the standard is yet to be ratified, do they even exist yet, if so i would love to be sterred in the right direction.
My suggestion, in case you can't find 0.1 Class CT you may test those available CTs then put % of correction into the ITC Instrument Transformer Correction module pleas ION Reference for more detail.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!