I have a question about BCPM split-core type CT amp ratings.
I have a project that has many 250A branch circuits. BCPMSC E-type meters would be suitable for a few of their panels . Except that according to the BCPM datasheet, split core branch CTs are only available up to 200A. However the specifications for the split-core branch CT and split-core main auxiliary CT seem to be the same - 0.333V output.
BCPMSCCT3 200A split-core 1.8m lead
LVCT00302S 300A split-core 0.333V output
Thus, my question is, can I use the 300A split-core CT (LVCT00302S) on my BCPM branch circuits?
Unfortunately, the branch input are using current mode CTs and not LVCT. So you cannot do this substitution.
I will check what we can offer to meet your needs.
This project we are working on has 5 panels that have multiple branch cirucits requirements.
22, 14, 14 ,8, 21 branches, (3-phase 380V, 100 ~250A)
Please let me know if you have any suggestions.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!