PM8240 inform alarm in PME 8.1 software " DAN6 Limit Exceeded 3". So, What is the DAN6 Limit Exceeded 3. and Where I can setting value DAN6?
The DAN6 is referring to the "Disturbance Analyzer Module #6" which in the default framework is used for Current Swell alarm detection.
The default settings is for 155% over Current Nominal (which by default is set to 5 Amps) with a reset of 145%.
Go to the Alarm -> Sag/Swell and modify the I Swell Pickup limit or modify the Nominal current to the appropriate value.
The other number at the end probably refers to which of the 3 phases is exceeding the pickup limit (Phase A = 1, Phase B = 2, Phase C = 3) but you should check the ION Reference to be sure.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!