We have a case wherein we need to allocate for both Harmonic Filtering and PF Correction. We intend to set the priority as 100% to Active Harmonic Filtering and 0% to PFC Correction. As per the tabulation and explanation provided in the manual, we are understanding that
"With Harmonic priority set to 100% the unit will output all current necessary to correct the harmonic content. Any output capacity left over will be used to correct PF and/or load balancing:
In our project the requirement is of 1004A as per the simulation study. We need to provide 300A: 3 Nos, 200A: 1 No. totalling to 1100A.
So based on 100% Filtering priority, once the requirement of 1004A is reached, will the unit deliver for Power Factor Correction the balance current available.
Alternatively whats the operation philiosohpy if we use the 90% Filtering and 44% Correction settings
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!