01.03 no of ABB VSD is connected to the AS-P via Modbus-RTU as slave Devices.
02.These VSDs are going to control via BMS.
03.The Control Point Configuration has attached here.
01.These VSDs must be operated as BMS command after a power failure
In first startup, the VSD does not operate according to the BMS Command. But after one more start & stop command, it started to operate properly via BMS. It occurs mainly after an power failure. But ABB VSD Vendor exhibited this function using ModBusPoll software. First he commanded to the VSD & shutdown Power of VSD. After powerup the VSD again, it was operated with the command. But this was not happend in Struxureware.
Please give me a solution as soon as possible.
As my observation, this VSD vendor, initially configured Modbus operating point(Register) as a reable & writable point. But it did not worked. Then he configured that point as only writable point & it operated properly
Would be more than happy to help.
I seem understanding that your Modbus communication issues with ABB VSD, are in the scope of Building Management Systems, for HVAC control aplications (and not Industrial Automation Systems).
If I am right, could you please tell me what is or what are Schneider Electric BMS controller or server ranges involved?
Power & Building Exchange Community Manager
Lately saw your previous post, explaining your issue, I could understand.
So, will connect with you through private message, as this forum is Industrial Automation focused.
Power & Building Community Manager
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!