the triac output in my MNB 1000 is not switching to 24 vca, the triac led is red, and the WPT is showing the output ON
it happens in my 4 new MNB 1000.
Sounds interesting - sorry to ask like this, but, what did Technical support say?
Hi again 🙂
If you had no chance to contact us, this is a start: https://www.schneider-electric.com/en/work/support/country-selector/get-support.jsp
the issue was solved,
The AC voltaje to triac outputs is sourced externally, in this case is not sourced from the controller.
Please post TAC I/A Series related questions in the TAC I/A Series forum (https://exchangecommunity.schneider-electric.com/t5/TAC-Vista-Forum/bd-p/tac-vista) so that it is seen by the correct audience,
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!