This was originally posted on APC forums on 1/3/2012
we purchased 4 SMT3000RM2U ups models. when the units arrived i noticed they are specs for 30 amp wiring/breakers. the problem is that the location only has 20 amp wiring/breakers. the switches that will be running off the SMT3000RM2U will not be at full loads anytime soon if ever. can i replace the plugs to a 20 amp type and use until we can get 30 amp wiring done with out any issues for now?
This reply was originally posted by Angela on APC forums on 1/3/2012
this should help as long as you are aware of local code and understand the limitations in doing it - http://nam-en.apc.com/app/answers/detail/a_id/184
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!