>>Message imported from previous forum - Category:ClearSCADA Software<< User: florian, originally posted: 2018-10-25 20:36:45 Id:308 This is a re-posting from the obsoleted (October 2018) "Schneider Electric Telemetry & SCADA" forum.
**_rnishimura:_** **_I am having an issue where the communications do not allow me to view exact start/stop times of pumps. So I programmed the PLC to store the latest date/time values each time the pump starts and stops and able to read that into ClearSCADA._**
**_Is there a function that will allow me to insert additional start (1) and stop (0) values to the history of the RunningStatus point at the stored data/time values to give a more accurate trend?_**
AWoodland: There are a couple of ways, i.e. use PresetTimestamp (updates current time but limited to internal point types) or LoadDataValue/LoadDataValues/LoadDataValuesEx that doesn't update the current value of the point but inserts directly into the historic, and works for all point types that have historic enabled