The Erie Classic style valve and actuator assemblies were built where the actuator was permanently mounted to the valve. The newer Erie PopTop style valve and actuators are built so the actuator can be removed and replaced while the valve stays connected to the pipes. Therefore, PopTop style actuators are not compatible with the Classic style models.
For the Erie Classic valves, their are rebuild kits available, see attached. If the valve is sweat end, replacement with an inverted flare style valve body can be an easier replacement option due to the inverted flare union fittings and longer overall length.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!