IEC61439-1 doesn't warrant for short circuit performance evaluation under the following conditions:
For further information on the topic, kindly refer to clause 10.11.2 under short circuit performance.
Principal Technical Expert
IEC 61439 standard has clearly defined 12 tests ( 7 Verification of Constructional and 5 Verification of Performance )
These 12 type tests are must to be conducted as per IEC guidelines.
Based on the successful completion of the 12 type test, the product is certified as IEC 61439 verified.
To specifically answer to your question on "Short circuit" withstand test,
Yes Short circuit test is one of the 5 performance test that a LV panel to be tested.
Hope i have clarified your question
please feel free to reply and also do share further inputs which can enable your business and differentiate with competition technically .
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!