From the available inputs;
let us see how to determine the 'smallest allowable cross sectional area' of the circuit conductors.
Directly in Ground
*Some of the inputs are assumed to provide in this example; and they were neither received from the user, nor from the environment.
As the THDi is > 33 % (that is THDI = 48 %). So, the Size-determining" live conductor is Neutral
This circuit is assumed to be protected by the circuit-breaker.
So that the K3 =1.0
For 40°C and with the insulation XLPE. F1 = 0.85
There is no additional touching circuits i.e. total no. of circuits is 1
F2group = 1.00
THDI >45 % = THDI = 48 % à f3NeutralTHDI = 1.00
Installation method = in Ground -> Rth = 2.0 K.m/w
f3RthSoil = 1.12
Correction factor f
f = 0.85 × 1.00 × 1.00 × 1.05 × 1.00 = 0.952
The overall correction factor is determined by multiplying all 'the available correction factors."
Theoretical Iz’ = (K3 x IB) / (F x N live) = (1.0 x 288) / (0.952 x1) = 302.52 A = 303 A
The conductor selection is done from the given Table B.52.5 Column 8
185 mm2 will be able to carry 324 Amps
240 mm2 will be able to carry 375 Amps
Considering the +5% of tolerance, It would be recommended to consider the size as 185 mm²
K3(Correction Factor based on Protection Device)
F1(Correction Factor based on Temperature)
F2(Correction Factor based on Group of conductors)
F3(Correction Factor based on THDi)
F3(Correction Factor based on Soil Resistivity)
K user(Correction Factor defined by the user)
Iz (A) considered from the table
Theoretical cross sectional area Ph (mm²)
1 x 185 mm²
Theoretical cross sectional area Neutral (mm²)
Theoretical cross sectional area PE (mm²)
1 x 95 mm²
That's really informative answer.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in