This question was originally posted on DCIM Support by Manuel M Albornoz on 2018-03-14
Is there an updated Modbus TCP or SNMP DDF file to see all Symmetra MW sensors in StruxureWare?
This answer was originally posted on DCIM Support by Navaneethan Rajendran on 2018-03-14
Goto Device Support and search for the device, and click on "I Want it Too" to get the latest ddf.
This answer was originally posted on DCIM Support by Balaraman Jagadeesan on 2018-03-15
It is recommended to discover the Symmetra MW via Modbus Over TCP option in DCE software to view the parameters in DCE software for Symmetra MW UPS. As far as I know, Symmetra MW UPS parameters can not be monitored via SNMP as the way we do via Modbus RS485 or RTU.
You need to use the Symmetra MW UPS's Modbus RS485 connectivity option. Symmetra MW UPS needs to be discovered in Struxureware DCE software by using Modbus Over TCP option. You will need Modbus RS485 to Modbus Over TCP converter to discover the Symmetra MW in DCE to view all the parameters.
As you can see, Symmetra MW Modbus DDF file is already present in DCE software.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!