This question was originally posted on DCIM Support by Sergio on 2017-06-20
Is it possible to monitor an SDMO generator (Telys 1 modbus RS485 controller) using an EGX150 gateway with DCE? What else is needed?
This answer was originally posted on DCIM Support by Steven Marchetti on 2017-06-20
That should work...as long as you can properly poll the device via IP when you connect it to the gateway. You also need a DDF or device definition file. If you go to the device support menu, you can search for the specific device. If it's there, click on "I want it too" if not, you can request they create one. I've searched for this and it appears there is an SDMO Telys2 but not a Telys1. You may have to request a new one if the registers are different.
This comment was originally posted on DCIM Support by Sergio on 2017-06-20
Perfect, thanks for your help, Steven
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!