This question was originally posted on DCIM Support by Enric Climent on 2015-10-29
What is the best way to manage the netbotz sensors with DCE? Actually I create a virtual sensor for each netbotz sensor and then I create a DCE threshold of this virtual sensor? It's that correct or there is a best way?
This answer was originally posted on DCIM Support by Steven Marchetti on 2015-10-29
The NetBotz devices themselves are responsible for the alerting of the NetBotz sensors. This was by design since the old NetBotz Central. If Central went down, the device could still alert. You can also configure NetBotz thresholds and alerting through DCE's Device->NetBotz Appliance Configuration menu.
If you need to have DCE alert for these sensors for some reason, the only way to do this would be to create virtual sensors at this time.
This comment was originally posted on DCIM Support by Enric Climent on 2015-10-29
I'm using the virtual sensors for DCE alerts.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!