This question was originally posted on DCIM Support by Gono on 2018-07-25
I now on testing Netbotz NBRK570 for SMS Alert
i ever install it before with ZTE MF 100 and automatocaly detect after reseting Netbotz
but now i used other ZTE MF 100 (software version PCW_IM2IDP 18DV1.0.0B01) can't detected, even i already resetting Netbotz using hyperterminal (soft reset coomand)
please help what we must check and do to solve it.
This answer was originally posted on DCIM Support by John Thompson on 2018-07-25
As per KBase FA158359, the 570 should be using BotzWare 4.2 or later in order to support that modem. Please check that the BotzWare is u to date.
If you had one of those modems working before, check if it was using different firmware to the one you have now.
This comment was originally posted on DCIM Support by Gono on 2018-07-25
My 570 using Botzware 4.6.2, atached captured from advanced view
the problem is i dont know how to change Modem firmware, or what firmware that can connected.
This comment was originally posted on DCIM Support by John Thompson on 2018-07-25
Check if the modem is detected in a Windows PC, just to confirm that it is actually working ok.
Try the modem in all of the USB ports in the 570. If you have other devices in the other USB ports, maybe try removing them, and then connect the modem on it's own.
If that doesn't work, you may have to try a format of the 570 itself, using the instructions in FA158175, assuming you haven't done this already.
The last thing to try is to reflash the BotzWare using the TFTP procedure, just in case there is any corruption there. This is covered in FA176133.
This comment was originally posted on DCIM Support by spezialist on 2018-07-29
Dear Gono ,
Tell us, please, did you solve your problem or not?
This comment was originally posted on DCIM Support by Gono on 2018-07-30
Until now the problem is not finished yet. my question, is the ZTE MF 100 driver different? because there are some modems detected and not detected. we've tried on the computer and the modem is working normally.
This comment was originally posted on DCIM Support by spezialist on 2018-07-30
Dear Gono ,
I'm also interested in this topic...
More details about the current status of the modem can also be found on the special debug web-page of your NetBotz appliance: http://NetBotz_address/pages/modem.html
This comment was originally posted on DCIM Support by asep Supriadi on 2018-08-16
site can’t be reached
This comment was originally posted on DCIM Support by spezialist on 2018-08-16
Dear asep Supriadi,
I hope, you certainly replaced phrase NetBotz_address with the real IP-address of your NetBotz-4.x appliance?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!