This question was originally posted on DCIM Support by Carsten Hjuler Madsen on 2018-08-30
If I have 2 ATS in 1 Rack, I can't config the Power Dependency on one of them.
This answer was originally posted on DCIM Support by Jef Faridi on 2018-08-30
It is by design only one rack ATS can be connected to a pair of rack pdu's. It is mainly because of the predicted power and power sold estimated load strategies - they treat primary and secondary rack pdu's as if they were paired. One rack pdu cannot be paired multiple times.
This comment was originally posted on DCIM Support by Carsten Hjuler Madsen on 2018-09-03
We have a lot of rack with 2 ATS install and only 2 Rack PDU.
This answer was originally posted on DCIM Support by MANCINO Rocchino on 2018-11-14
when you talk about ATS, also with Ap771?Because we also have a lot of ATS in racks for mono powered appliances
This answer was originally posted on DCIM Support by Christian Riis on 2018-11-26
Suggested workaround: Model one ATS with the combined sum of the outlets of all the other ATSs. Connect this ATS to the rack PDUs and the server equipment to the ATS.
Add the other ATSs as "dummy" ATSs, that is without connecting any equipment to them. This way the inventory reports will be valid.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!