This question was originally posted on DCIM Support by Andres Alfredo Gonzales De La Cotera Herrera on 2019-05-28
I have presented a problem after updating the firmware of the UPS,
since it does not recognize the temperature sensors and shows me the following alarm:
The communication between the local management and the integrated environmental monitor in NMC was lost.
This comment was originally posted on DCIM Support by Balaraman Jagadeesan on 2019-05-28
May I know your UPS model number?
What is the current firmware that is shown on NMC web interface?
Can you please share the firmware version screen shot?
Are you able to view the other UPS parameters correctly?
This comment was originally posted on DCIM Support by Andres Alfredo Gonzales De La Cotera Herrera on 2019-05-28
Yes, the first model : Smart-UPS SRT 10000
Smart-UPS RT 6000XL
Yes and I tried to reset the alarm but it still stays the same.
Thanks for your time.
This answer was originally posted on DCIM Support by Justine Chester on 2019-05-28
Both of your UPS uses the SUMX NMC firmware. I would recommend updating these NMCs (network management card) directly using the executable firmware update tool that can be downloaded from the link below:
There is a chance that the firmware that was recently updated/applied to the UPS network management card has not been uploaded successfully, causing this issue. Reapplying the firmware or updating it to the latest available version usually corrects this.
I hope this helps.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!