This question was originally posted on DCIM Support by josep.vilar on 2018-01-29
We have DCE 7.5 managing 5 Symmetra 160K. When we try to run kWh report, we can't select any sensor so we can't run kWh. Other reports run properly.
How we can do to get kWh reports?
Thanks in advance.
This answer was originally posted on DCIM Support by Balaraman Jagadeesan on 2018-01-29
Are you able to view Kwh value as the device sensor value in DCE software for Symmetra PX 160 K under view device sensors value?
In order for the DCE to generate the report of the sensor values, the sensor value should be present in the device for which you are generating the report.
As far as I remember, Symmetra 160 K UPS does not have Energy Kwh value reported via SNMP. If this sensor value is not present, then DCE will not be able to generate the report on Kwh.
I hope it answers your query.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!