This question was originally posted on DCIM Support by Muhammad Shahzad on 2019-06-21
Symmetra PX ups output current is L1-22A showing on its user display while i had checked physical with clamp meter which in 60Amp. Means L1-22Amp reading is incorrect, I have replaced it MIM/RIM for its rectification but this issue is still exist. Please tell guide is there any other step to rectify or its malfunctioning of Current Transformer.
Solved! Go to Solution.
This answer was originally posted on DCIM Support by spezialist on 2019-07-28
Dear Muhammad Shahzad,
I suspect, that this problem is related to the malfunction of the current transformer in phase L1. Six months ago, I had a similar problem.
Conclusion: You need to contact the =SE= local service center staff to replace defective parts in your UPS.
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!