This question was originally posted on DCIM Support by Shoaib Maqsood on 2019-04-08
we are going to install the Rack monitor 450 and 550 at our client site .
We will connect the rope leak with rack monitor 550 or 450.
As Rope leak will generate the alarm, a shut of /Switch off command will be sent to fresh water valve.
This answer was originally posted on DCIM Support by Steven Marchetti on 2019-04-08
Any sensor, including the leak rope sensor, is capable of triggering any alert action on the NetBotz appliance. If you're connected to an output relay or an outlet on the appliance, those can be configured to be triggered by the sensor. Assuming this is for emergency situations and not something that is expected on an hourly basis or something, it should work fine. I state this because for one thing, the leak rope takes a while to dry and it takes a while for the alarm to clear. If it was for something to be done on a regular basis instead of an alert situation, I'd recommend a float of some sort if possible to turn off the water.
Is there something more specific you're looking for?
Discuss challenges and get support in energy and automation with 30,000+ experts and peers.
Over 10,000+ support articles are available to help you find answers to your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!