I need to reset and close backer using the modbus command, now i already connect with sepam suing the ACP949 device. i can read the data from sepam, but my issue is how can i reset sepam using the modbus.
You might find your answer in the product documentation: https://download.schneider-electric.com/files?p_Doc_Ref=SEPED303003EN
Otherwise, I'd suggest reposting your question in the Building Operation forum.
Have a question? Please contact us with details, and we will respond.
Look through existing questions to find popular answers.
Want to know more about Exchange and its possibilities?
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!
Register today for FREE
Already have an account?Log in