This question was originally posted on DCIM Support by Shoaib Maqsood on 2019-04-02
Is the rack Monitor 250 compatible with leak rope (0308) or not?
This answer was originally posted on DCIM Support by Justine Chester on 2019-04-02
Netbotz 250 is incompatible with NBES0308 (Leak Rope Sensor). This sensor is only compatible with the Rack Monitors 450 and 570.
For additional information, you can refer to the Netbotz Compatibility Chart from the link below:
I hope this helps.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!