This question was originally posted on DCIM Support by Balaraman Jagadeesan on 2017-01-11
Struxureware Data Center Expert allows the user to generate the following reports:
I hope the following procedures will be useful for those users who want to generate reports in DCE software.
Login to DCE client program.
Click on Reports pane
Select the sensor type for which you want to generate the report. For example: To generate a temperature sensor report of any or more of the devices, click on Temperature Sensor type. If you want to generate the report of UPS output power(Watts or KW), then select the sensor type as shown below.
User can select either a date range or a time relative report for the devices with further requirements of sensors & groups
The graphical trend report can be exported by using the export option as shown below.
Summary report also can be seen by using the summary report option.
Raw Data also can be viewed and exported as shown below.
This report also can be saved a pre-defined report by using the Save and Save As buttons options, and the pre-defined report will be shown under Saved Reports.
DCE Web Interface also allow you to generate the similar reports on the Web browser/Interface as shown below. The Pre-defined reports also will appear under Saved Reports as shown below.
To view the Pre-defined saved reports, Click on Saved Reports tab to view the Saved Reports list as shown below.
Here is the procedure to view the Past history alarms view of the device(s) or Group of devices(s).
Step 1: Select the device for which you would like to download the Alarm History
Step 2: Select the period and then click on Search
Step 3: All the alarms history for the device will be shown in the box. And then click on the folder option as shown below and select CSV to export the History of the Alarms.
I hope this helps.
This comment was originally posted on DCIM Support by Stine Hansen on 2017-01-17
Thanks for sharing!
This comment was originally posted on DCIM Support by alexander_myers on 2017-01-24
This is great. Thanks for the instructions!
This comment was originally posted on DCIM Support by Balaraman Jagadeesan on 2017-01-24
You are welcome Alex!
This comment was originally posted on DCIM Support by Sunil Kumar on 2017-08-28
It's really very effective one...
This comment was originally posted on DCIM Support by Shoaib Maqsood on 2018-10-04
I have installed the 5 door sensor. 2 door sensor generate the reports. But the remaining 3 sensors are not generating the reports.
Discuss challenges in energy and automation with 30,000+ experts and peers.
Find answers in 10,000+ support articles to help solve your product and business challenges.
Find peer based solutions to your questions. Provide answers for fellow community members!